Changing an I/NET DI to a DA does not show up in StruxureWare Building Operation Workstation
TAC I/NET, SmartStruxure Solution
I/NET SmartStruxure Integration
After integrating I/NET to SmartStruxure the designed intent is to allow all point name changes and alarming to be done in SmartStruxure workstation. If you delete a point and re-create it using the same point address, point name but a different point type, the change will not show up in SmartStruxure.
To successfully change an I/NET point from DI to DA:
- Delete the Point using the I/NET Resident I/O Editor
- Re-create the Point using the I/NET Resident I/O Editor using the new point extension DA. YOU MUST change the point name in some way.
- Perform a Station Save
- Open Building Operation Workstation
- Right Click on the Controller and select Update.