The BDelay object from the LonWorks jar conversion library intermittently shows very large "remaining time" causing logic issues.
TAC I/A Series
The BDelay object does not initialize the time remaining properly under some conditions.
In the Lib jar - programObjects - hvac folder there is a program called DelayedOutput.sns. This program can do the delayed on and off function but will need to be enhanced if the time remaining output is required.