An Enumerated schedule created under the BACnet Interface application folder will not control a digital value (Occupancy) in a b3 controller.
Other b3 controllers are handling this with no trouble.
- Variable Connectors
Broken variable connectors.
- Deleted the bindings and performed a Repair References on variable connectors.
- The digital value responded properly once the schedule binding was re-established.