Job site has a Niagara G3 station integrated with several Xenta 301 controllers. Can the Menta programming tool be used via LON tunneling through the station to re-program the Xenta controllers on an as-needed basis?
TAC Vista, TAC I/A Series
Field request for ease of programming
Tunneling via a Niagara G3 station to Xenta controllers is not possible. A direct-connection is required.