BACnet device instance number in SmartStruxure
SmartStruxure 1.3, 1.4 BACnet Integration
The BACnet device instance number is unique within a BACnet internetwork. There may be a need to find out or change the device instance number to ensure there are not duplicates.
When a BACnet Interface is added to an AS or ES, the AS or ES will become a BACnet device and it will have an instance number (automatically generated or manually assigned).
- To check an ES or AS BACnet device instance number, go to the properties of the BACnet Interface and then the Advanced tab. The device instance number is the Object ID.
- To check a BACnet device, go to the properties of the BACnet Device and then the Advanced tab. The device instance number is the Object ID.
The valid range of instance numbers for a BACnet device is 0 to 4194302.