A new computer has been configured as an InVue Client computer. In Viewer, when displaying a typical graphic screen, the dynamic values for each OCX is replaced with the words "Access is Denied".
What causes this message and how can it be corrected?
TAC I/A Series
Wonderware for Intelligent Buildings (WIB)
Primarily a Windows permissions issue or incomplete communications setup.
Try each of the following to correct the problem:
Make sure DCOM is enabled (Start -> Run -> dcomcnfg) and running on both the client and server computers.
Use "telnet" command to see if port 135 is open and available for DCOM.
Use dcomcnfg.exe to modify its settings:
- On Default Properties tab, verify that "Enable Distributed COM" is checked, default authentication level is "Connect" and Default impersonation level is "Identify"
- On Default Security tab, Default Launch Permissions - click Edit ... button, verify that the Administrators group is shown and has "Allow Launch" permission"
- On Default Security tab, Default Configuration Permissions - click Edit ... button, verify that the Administrators group is shown and has "Full Control" permission"
Windows login account for the client pc must exist on the server as well -- same username and password -- administrative privileges mandatory
Ensure wwuser.exe (factorysuite/common folder) reflects the local computer name and administrative user account
Re-do the DDE Shares as outlined in Tech Bulletin 02-26 on the client computer.
Turn off any firewall and disable/remove anti-virus / anti-spam program or service.