Configuring a Smart Sensor in a B3 controller in StruxureWare Building Operation using a simple script program to display temperature. The temperature does not display in the Smart Sensor LCD.
Automation Server with B3 controllers
SmartStruxure 1.4 attaches a _AV, _BI, etc. to the BACnet name
- Remove the _AV, _BI, etc. from the LCDDisplay BACnet name
- Download the controller again
- The display functions as suggested