It is not possible to select a "Trend 10K3A1" thermistor when configuring a central IO input point
Building Operation WorkStation
The specific thermistor type has not been added to SmartStruxure
Configure an input as a resistive with reliability level, electrical scale and engineering scale set to:
- Upper/Top: 0
- Lower/Bottom: 587628
Then use a Function Block program or Script program to convert from resistance to °C.