Configuring the SSC to use Comm Port B on an SSC.
Hosted Instance Version 2, Version 3
The SSC is not configured to work on Comm Port B for the RS-485 connections, all communications to downstream devices are done through Comm Port A. If you have done so and it functions, please note that this is not supported.
All communications on an SSC for RS-485 in Accessxpert needs to be done on Comm Port A.