- Need the Spectra Mini to move to a preset location after power up.
- Need the Spectra Mini to start a pattern after power up.
Pelco Cameras, Pelco Video Management
- Spectra Mini (analog)
After a power surge the camera does not returns to the position it was left at.
Configure Power Up Action
Note: Power Up action settings defines a specific activity to be perform in the event the power to the dome is cycled.
Enter the Spectra Mini dome settings by programming preset #95.
Scroll down to Dome Settings.
Scroll down to Power Up.
- Adjust the Power Up Action setting by selecting one of the available activities.
* The following activities are available:
NONE No action
AUTO (default) The dome resumes its prior activity or direction before the power outage.
AUTO SCAN Dome starts auto scan operation.
RANDOM SCAN Dome starts a random scan operation.
Frame Scan Dome starts a frame scan operation
PRESET 1 Dome goes to preset 1.
PRESET 8 Dome goes to preset 1.
PATTERN 1 Dome goes to pattern 1.
Access the program menu (Dome Settings) of a Spectra / Spectra mini, Esprit PTZ camera sending the preset 95 command.
How to program a power up action on Spectra Dome using a KBD300A.
Configuring power up action on Spectra Mini, Spectra IV dome using DS ControlPoint.