Documentation supplied with new UNC, ENC, or Jace 8000 was discarded. Is there a way to determine the default, factory defined IP address for the Ethernet port on the controller?
TAC I/A Series
I/A Series (Niagara) R2 UNC
I/A Series (Niagara) G3 ENC
Niagara N4 or G3 Jace 8000
Lost or discarded document, shipped with controller, that contained the configured IP address.
The default Ethernet IP address for an I/A Series (Niagara) UNC or ENC is based on the serial number and type of device.
For a UNC or ENC the default address is 192.168.1.14X where X is the last digit of the device serial number. The default serial number is found on a sticker on the controller circuit board. This sticker has the full model number, date code and serial number of the controller. The serial number is preceded with S/N:.
The subnet mask is 255.255.255.0 in all UNCs, ENCs and Jace 8000
The default address base address (192.168.1.140) is the same for all UNC-410, UNC-510, UNC-520, ENC-410 and ENC-520 controllers.
The default IP address a Jace 8000 for PRI (LAN1) is 192.168.1.140. SEC (LAN2) is by default disabled.