In an existing Niagara G3 ENC-520, version 3.3.22, a station will not load after a reboot. Prior to the reboot, it was functional.
The error in the Application Director Output is: "javax.baja.xml.XException: InValid LonFloat: '2.788969984E9'.
The only way to get the station started is to modify it offline and remove the logic for a LON integration to an ONICON flow meter. Then, the modified station gets installed and, once the station is started, the same logic that was removed is added back.
TAC I/A Series
Niagara G3 version 22.214.171.124
A bug in the lonworks.jar file for version 126.96.36.199
Installed the lonworks.jar file from version 3.3.34 which is available below (password=niagara).