What configuration is required for a Multical BACnet heat meter
Andover Continuum, Field Devices, SmartStruxure Solution
Schneider Electric (Kamstrup) heat meter connected to a Continuum or SmartStruxure system on MS/TP.
Setup information required
With the BACnet interface card fitted in the Multical meter it is a native BACnet MS/TP device.
Connect it to the AS or bCX1 depending on your system and Learn/ find BACnet devices. It should appear online and allow the objects to be uploaded.
A typical unit like the Multical 602 will contain 12 Analog Inputs for all of the information from the meter.
The Meter will operate at 9600, 19200, 38400, 57600 and 76800 Baud rates and autobaud to the connected system.
For the Datasheet Click Here.
For the BACnet PICs statement Click Here.
Further information on the heat meter range is available on the Extranet: http://buildings.schneider-electric.com/Navigate?node=9994