Importing a VisiSat pointslist StruxureWare reports a limit issue and suggests the import is complete.
Satchwell MicroNet, SmartStruxure Solution
StruxureWare Building Operation 1.3/1.3 SP1
On one of the VisiSat points being import, the alarm limits have been incorrectly set.
Although StruxureWare Building Operation 1.3/1.3 SP1 reports that the import completed in X minutes and X second, the import would have failed to complete due to the stated issue.
Unfortunately the reported limit issue can effect 100 points or just the 1 point.
The specific point or points identity is not highlighted in the trace file.