The Modbus master / client is unable to read the address of a 32 bit Modbus register in a Building Operation server
StruxureWare Building Operation server as a Modbus server / slave
When a Modbus master or client reads a 32 bit Modbus value, it will be reading 2 consecutive 16 bit registers. An error will occur if two 32 bit Local Modbus Registers are created in Building Operation using consecutive register addresses.
When configuring 32 bit Local Modbus Registers in Building Operation, the next register address should not be used. Create the next Local Modbus Register using the 3rd available Modbus register address.