Unable to write strings (messages) to the "Long Screen Message Text" and the "Short Screen Message Text" points on the SE8000 Room controller using an Automation Server (AS) through BACnet.
SmartStruxure Solution, SmartStruxure Lite
Multi Purpose Manager
SE8xxx Room controller
SER8300, SE8300, SE8350
Ex. Viconics branding VT8000 Series
SBO does not support ".csv" BACnet objects.
The Short Message can be written to the SE8000 room controller by populating the "Location" Property with the message
The Long Message can be written to the SE8000 room controller by populating the "Description" Property with the message
The message however will not get displayed until the "Display Long Screen Message" has been activated.
Optional: you can also choose the color of the long message background by changing the "Long Message Background Color".