What binding methods can be used and how is the data transferred when binding objects between b3 controllers?
When binding objects between b3 devices/controllers, the type of b3 Objects being bound will effect the properties of the binding
When binding between two b3 devices, several methods can be used:
b3 Value/Point to b3 Value/Point - The data goes via the Automation Server and speed/rate is set in the Transfer Window, thus more bandwidth used and communication is lost if the Automation Server fails
b3 Script to b3 Value/Point - The data goes direct using BACnet COV subscriptions, thus less bandwidth is used