UNC 410 AI point no longer reads the input properly.
TAC I/A Series
Input is not reading the input value properly.
- Verify that the NDIO object for that physical point is still programmed correctly -- 10K Thermistor, Resistance, 0-10 VDC, 4-20 mA.
- Verify that the input sensor or device has not been damaged and has not been replaced with an incorrect replacement.
- Verify that the physical input port has not failed or become damaged by either programming an unused input in place of the failed port or temporarily swap the input device/sensor to another port. You may need to swap the input with another currently used input if none are available.